Question about Heating & Cooling
The motor continues to run even if the room temperature reaches to its level. I think there is a problem in the timer of the motor. Can you help me about this matter.
Look for a 'power saver' option in the controls. It should turn the fan off when it is not cooling or heating.
Posted on Nov 26, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
On the thermostat if its a manual on then pop the cover off and look for a small dial with numbers on it. Take and move it tpoi a higher number than whats it is set at. Its called a heat anticipater and is supppose to make it so that the unit does not oveshoot or under shoot like what your experiencing. If its a digital oine then you are going to have to configure the setting in the insdtallers menu.
Posted on Dec 21, 2008
unfamiliar with watt restrictors.
heat strips have 2 safety devices, a thermal overload, they get to hot they shut off, cause not enough air flow increase fan speed this device is auto reset. a fusible link a fail safe to thermal over load, no reset and sometimes replaceable. if this does not help would like to ask you a few questions. one of the buildings i take care of has 200 + reem/ ruuds all electric heat. if a part is defective replace, please do not by pass. safety frist.
Posted on Mar 07, 2009
The unit is designed to run the indoor fanmotors continuously when in cooling mode on both indoor units (evaporators). The reason is that this circulates the air and the temperature thermistor or sensor is able to sense return air temperature and in turn start or stop the outdoor unit and compressor as required according to the setpoint temperature. The reason for either unit not reaching setpoint temperature can be a couple of reasons. A) Incorrect design - the unit may be too small for the application. You can calculate this roughly at 650BTU per square meter of room in a relatively warm ambient climate. Or secondly B) The outdoor unit has leaked and is short of refrigerant. You can check this when the outdoor unit is running by feeling the thicker copper tube on the right hand side of the unit. This should be cool to cold. If no temperature difference is felt, it is short of refrigerant. Hope this helps you. Goodbye
Posted on Mar 20, 2009
Tips for a great answer:
Jul 10, 2007 | Sharp CV-P09FX Air Conditioner
Nov 02, 2013 | Midea Heating & Cooling
Jul 28, 2011 | Danby DDR5009EE Dehumidifier
Jul 21, 2011 | Whirlpool ACQ158XP Wall/Window Air...
Dec 15, 2010 | 1998 Ford Crown Victoria
Apr 16, 2009 | Heating & Cooling
Aug 11, 2008 | LG LS-L1210CL Mini Split Air Conditioner
Sep 24, 2007 | Honeywell /KAZ HOME ENVIRONME HZ-705 7Fin...
29 people viewed this question
Usually answered in minutes!