Question about Heating & Cooling
I bought used heater. It worked at shop but when i come to home, i power up it, it power up but didn't get ignite. tried both home gas and LPG but it didn't get flame out. It look like it keep on inginiting.Please advice.
A natural gas heater can only burn natural and vice versa unless there are changes such as orifice and regulator. They can easily be converted to use either fuel, but you have to know what fuel supply you have, and what the appliance is set up for. Since you've already tried LPG, if it turns out the appliance is natural gas, then replace the spud (burner nozzle) before trying to operate it again. LPG cannot pass through the small nozzle hole in a natural gas appliance.
Posted on Dec 08, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
You may have one of two problems; The pilot orifice is very small and allows only a limited flow and any air trapped in the gas supply takes some time to bleed out while you are holding down the pilot button. Or the pilot orifice may be plugged in which case you would have to replace it.
Posted on Jul 10, 2008
Tips for a great answer:
Jan 21, 2017 | Heating & Cooling
Jan 25, 2014 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Nov 26, 2013 | Heating & Cooling
Nov 25, 2013 | Heating & Cooling
Jan 11, 2013 | Heating & Cooling
Dec 03, 2012 | Office Equipment & Supplies
Oct 20, 2012 | Heating & Cooling
Mar 04, 2011 | Heating & Cooling
Jul 21, 2018 | Heating & Cooling
248 people viewed this question
Usually answered in minutes!