Question about Powercom VGD-1000 (VGD-1000) UPS System
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds to me like you have a shorted cell in one of the batteries and the current limiting resistor on the charging side is out of tolerance (too low). Though it is more likely that they fail too high, they can go low in the event of overheating. I would check the resister with an ohm meter vs what is printed on it. It should usually be within 10 to 20% you can put one in series to limit the current, but you need a high current diode in parallel with it as no to limit the current to the inverter. I don't remember, but i think your model uses 2 12vdc batteries. You should replace all of its batteries and check the resister. Also, if there was a plastic insulator on the old mosfets you took off, you must have it on the new ones. this is to isolate the collector from ground. I home this helps,
Posted on Apr 19, 2009
Tips for a great answer:
Sep 15, 2013 | 2010 MV Agusta F4 1000 R
Apr 20, 2011 | Powercom Computers & Internet
Mar 15, 2010 | Powercom (BNT-1500AP) UPS System
Feb 07, 2010 | Powercom King Pro 1200VA...
Aug 26, 2009 | Powercom Computers & Internet
Apr 06, 2009 | Powercom (BNT1000AP) UPS System
Mar 31, 2009 | Powercom KIN-1000AP (kin1000aprm) UPS...
94 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: