Question about Water Heaters
Makes noise when heating
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Rheemglas Fury DV leaking?
I don't know if you have resolved your issue by changing the T&P relief valve. However, if you have replaced it and it appears to have resolved the problem ... it will most likely be only a temporary resolve. And what has happened, it that the water that was being relieved via the T&P valve is now unknowingly leaking / being relieved by a toilet or some other means.
The reason of the leak in the first place is that the most likely the water purveyor has recently installed a DCV (dual check valve) at or within the water meter location. Not knowing where you live, but we are in NC and these DVC's are being installed all over the country.
Basically, your home's plumbing system used to be an "open system" and not it is a "closed system". In earlier times, when the water heater cycled it heated the water, which cause the volume to thermally expand ... and the water was pushed backwards through the meter and it did not allow the water pressures to build. However, with the DCV installed ... now when the water heater cycles and expands water, with no place for the excess water volume to migrate, it now causes a hydraulic effect within the closed system ... which causes the water pressure to become elevated, ultiamtely being relieved at the T&P ...
Here are a couple of links from Watts ....that will help.
Locally, we have been on the Cross Connection / Dual Check Valve crusade since early in 1991. We concur that the check valves warrant installation. However the Buidling / Plumbing Codes are not up to speed with truly what is going and how much damage to personal property is occurring with failed water lines ... both inside the home and outside.
Best, Gary H.
Hestand Associates / email@example.com
Posted on Feb 01, 2009
SOURCE: How do I turn up
You have 2 thermostats inside of those covers, little things with a dial on them, turn them with a small screwdriver, Don't go too hot or you will be scalding everybody. Hope this helps.
Posted on Oct 05, 2010
SOURCE: I need anode rod for
Anode rods are generic and available from local plumbing supply store or internet.
Just cut it off so it drops into the tank without touching the bottom or sediment on the bottom.
If there is not enough room above the tank to install new rod, then buy anode rod with sausage links.
Open following link for Rheem parts: page 7 shows anode rods
Posted on Jul 04, 2011
Tips for a great answer:
Jan 07, 2018 | Water Heaters
Jan 14, 2015 | Water Water Heaters
Dec 14, 2014 | Water Water Heaters
Oct 14, 2011 | Water Heaters
Feb 28, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
Jan 01, 2011 | Rheem Water Heaters
Oct 05, 2010 | Rheem 80 GAL ELEC TALL Water Heater 6YR SC...
Sep 07, 2010 | Rheem 50 GAL ELEC TALL Water Heater 6YR SC...
Apr 16, 2009 | Rheem 40 Gallon FVR NATGAS Low WATER...
47 people viewed this question
Usually answered in minutes!