Question about Intertherm P3RA-048K Air Conditioner
I need more info is it both outside and inside and did you check your breaker
Posted on Aug 12, 2009
Manually bump the contactor whare the main power comes in with a insulated object isf unit starts then check for call from stat on stat wire from common to red 24v ac transformer good or see if indoor fan comes on next check call from stat common to yellow 24 v then look for low psi switch to see if it has it locked out could be low on gas
Posted on May 09, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 01, 2015 | Heating & Cooling
Sep 10, 2008 | Amana Heating & Cooling
on Dec 04, 2009 | Heating & Cooling
Feb 13, 2015 | Coleman Heating & Cooling
May 23, 2014 | Heating & Cooling
Aug 09, 2011 | Heating & Cooling
Jul 15, 2011 | Intertherm Heating & Cooling
Jun 13, 2011 | Intertherm Heating & Cooling
Jan 17, 2009 | Heating & Cooling
444 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: