Question about Panasonic Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: unit stops working - E1
I wrote the solution #1 and have an additional comment. This really does work!! I fixed my neighbor's AC unit by following the instructions for clearing the E1 code. The unit will not operate until the code is cleared. The page is titled: Customer assistance for air filters cleaning (E1 code) on Sharp Air Conditioners
Posted on Sep 07, 2007
some of the samsung units need to be reset if you have a new remote..contact your nearest agent for that aircon they will give you a code to type in using the remote control.if this does not work you might have to replace the internal pc board.good luck
Posted on Nov 25, 2007
SOURCE: LG Inverter A/C Unit LSJ092V-3
I would first check the condensate drain pipe. This can be done by blowing back into the drainpipe from outside. Not to worry it is not dirty or dangerous. Also make sure that your air filters are clean.
Posted on Mar 05, 2009
It sounds like your inverter is at fault. You will need an inverter tester ( most good service techs will have one ) to prove that the output to the compressor is correct. If the inverter is okay then it will be the compressor at fault with a location error or it is simply seized. A common fault that caused this was the eev remained closed (coil failure ) and caused the compressor to over heat.
Posted on Jul 15, 2010
Tips for a great answer:
Jan 31, 2016 | Panasonic Heating & Cooling
Jun 01, 2015 | Microwave Ovens
Feb 10, 2015 | Panasonic Single Split System - Wall...
Sep 09, 2014 | Microwave Ovens
Sep 08, 2011 | Panasonic Heating & Cooling
Jan 05, 2011 | Panasonic Heating & Cooling
Dec 09, 2010 | Heating & Cooling
Sep 10, 2010 | Panasonic Microwave Ovens
May 11, 2010 | Heating & Cooling
39 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: