Question about Heating & Cooling
Had the same problem with my system. turned out to be the thermostat in the hallway. Mine is an older electro-mechanical type with contacts that open and close as the temperature changes. (these type of thermostats click as you rotate the temperature dial) What had happened was the contacts had stuck closed even as the temperature rose and thus the boiler kept going. I cleaned the contacts with WD40 oil and everything is fine again. If you have the same type of thermostat this may be the problem. Be aware that if you or anyone else removes the cover of these thermostats there is live mains at the faulty contacts, be sure to switch off the circuit feeding this thermostat or remove/switch off the fuse in the main fuse box. Alternately you could replace the thermostat. If you have an electronic digital thermostat then this solution is not valid.
Posted on Dec 24, 2013
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Our Honeywell thermostat is model RTH6300B. Now that the weather is getting hot, we decided to put the centeral air on. Hot air keeps blowing out. I called Honeywell several times thinking that we had fixed the problem. It still is blowing out hot air. Also, my husband checked the wires. Has anyone else had this problem? Any ideas what it could be?
Posted on May 29, 2008
sometimes the furnace does a better job than anticipated, i wouldn't worry about it, especially if the furnace shuts off.
the setpoint is the temperature you want it to be
cycle lenghts are determined by how much recovery you are requesting. for instance, in the morning when you wake up, you want the temperature to be at its setpoint. what the thermostat will do is make the furnace run a limited lengths during the recovery process.
Posted on Nov 12, 2008
SOURCE: thermostat problem ?
If you start by looking on your gas valve, you should find the correct amperage to set the heat anticipator at. I am not sure if you have a forced hot water system or a steam system, but depending on the case, you may also have a second problem, which is easily addressed. If you have forced hot water, the upstairs baseboard/radiators may be airbound and need to be bleed. If you have steam, you may need to slow down the downstairs valves, and open the upstairs valves to get a balance. Hope this helps
Posted on Jul 09, 2009
You definetly have a control issue. However trying to diagnose the exact problems that you have would be very difficult without actually seeing the wiring. You defintely have a wiring/control issue but I cannot tell you exactly what it is without more info. Sorry, I would love to help you more...
Posted on Nov 13, 2009
Tips for a great answer:
Jun 23, 2014 | Heating & Cooling
Sep 10, 2008 | Amana Heating & Cooling
Nov 22, 2013 | Heating & Cooling
Sep 30, 2013 | Heating & Cooling
Dec 18, 2012 | Heating & Cooling
Nov 06, 2011 | Honeywell Programmable Thermostat Heater
Apr 10, 2017 | Honeywell Heating & Cooling
Oct 20, 2008 | Honeywell CT87B ROUND HEATING&COOLING...
May 22, 2018 | Emerson Heating & Cooling
114 people viewed this question
Usually answered in minutes!