Question about Honeywell L4064B2236 Fan/Limit Control Heater
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Here's my best shot.
Check the temperature settings for the fan switch.
The low OFF setting should be about 100 degrees.
The ON setting should be around 150 degrees and this is the setting that "makes" the ON contacts.
The HIGH LIMIT setting should be about 180 degrees.
If these are set, can you use a meter to see if the FAN ON contacts are closed?
Lastly, it appears that one hot line should go to one side of the blower and the other hot line should go to the bottom FAN terminal with the other side of the blower being fed by wiring from the top FAN terminal.
Good Luck. Gary
Posted on Feb 22, 2011
Tips for a great answer:
Oct 24, 2014 | Home
Oct 12, 2014 | Heating & Cooling
Sep 23, 2011 | Woods 59007 Decora Style 3015105 Minute...
Dec 22, 2010 | Woods Ind 59008 Digital Timer
Dec 21, 2010 | Heating & Cooling
Oct 30, 2009 | Goodman GMS90703BXA Heater
Aug 13, 2009 | Heating & Cooling
May 24, 2009 | Heating & Cooling
Jan 03, 2009 | Heating & Cooling
Aug 19, 2007 | Honeywell CT87B ROUND HEATING&COOLING...
21 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: