Question about LG Art Cool LA121HNP Split System Air Conditioner
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: my LG Artcool isn't working
CH61 means Condenser coil temp high due to non cleaning of condenser/over charged gas/non condensable gas.
Clean your condenser coil. If still problem rests, due to non condensable gas also there will be high temp. kHnce remove the gas, flush out the system and vacumize and then do gas charging.
Posted on Dec 10, 2010
Tips for a great answer:
Apr 19, 2008 | Heating & Cooling
Aug 31, 2011 | LG Art Cool LA121CNP wall/window Air...
Jun 16, 2011 | Heating & Cooling
Dec 10, 2010 | LG Heating & Cooling
Feb 12, 2010 | LG Heating & Cooling
Mar 11, 2009 | Connex 3300 240-Channels Base CB Radio
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
64 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: