Question about Humidifiers
Are there any ways to install a humidifier to a furnace that has no source of water. Are there water tank units that you could manually fill
I've never heard of a manually-filled furnace humidifier. We use a whole-house, stand-alone humidifier (manually-filled) and it works just fine. Easy to fill, easy to clean, easy to maintain. Even if there were such a thing as a manually-filled furnace humidifier, in the case you describe, I would much rather stay inside to fill my humidifier than get bundled up and step outside into the cold to do it. Hope you find a good solution. Good luck!
Posted on Nov 24, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Installation problem
I WOULD CHECK TO SEE IF YOU HAVE ENOUGH V/A OUT-PUT ON TRANSFORMER. I DONT KNOW IF YOURS CAME WITH ITS OWN TRANSFORMER. IF IT DIDNT YOU SHOULD HAVE A MINIMUM OF A 40 V/A RATING STAMPED OR PRINTED ON THE EXISTING TRANSFORMER. IF THE TRANSFORMER IS EXTREAMLY HOT ... YOU MAY NEED A 75 V/A TRANSFORMER WITH THE SAME VOLTAGES. INCREASING THE V/A CANNOT DAMMAGE ANYTHING IT JUST GIVES YOU MORE POWER WHEN EXCESIVE CONTROLS AND WIRING ARE ADDED TO A HVAC LOW-VOLAGE (24v) CIRCUIT. IF YOU LIKE YOU CAN CALL ME AT 727-363-7071. I AM A RETIRED HVAC&R CONTRACTOR WITH 45 YEARS EXPERIENCE. I HATE THE NEW SENSORS THEY HAVE TO ACTIVATE THESE NEW HUMIDIFIERS. I USE TO WIRE THE HUMIDIFIER TRANSFORMER (SUPPLIED WITH HUMIDIFIER) TO THE LINE (110V) SIDE TO THE LOW SPEED ON YOUR BLOWER MOTOR. THAT WAY THE ONLY THING THAT INTERUPTS THE CICUIT IS THE HUMIDISTAT. YOU NEVER WANT THE HUMIDIFIER TO RUN IF YOUR SYSTEM IS NOT "CALLING FOR HEAT". NEVER TRY TO ENERGIZE THE WATER SOLENOID THROUGH YOUR HEAT WIRE(USUALLY SMALL THE WHITE WIRE) FROM THE THERMOSTAT. THIS WILL RESULT IN BURNING YOUR HEAT ANTICIPATOR OUT ON THE T-STAT.
Posted on Apr 28, 2007
You can try installing the water line to your hot water if it is installed on cold line for more humidification. You should make sure your humidistat is up line 6" @least from humidifier for proper humidification measurement.
Posted on Mar 04, 2008
I am having the same problem. I have had my humidifier for about 5 years now and I just started having the problem where the water continuously flows through the solenoid. I took apart the solenoid by removing the fittings from both sides. When I did that, I noticed that there was a hole in the metal that allowed me to see through to the other side. Apparently, it had corroded and and broken through, allowing the water to pass through the solenoid without really going through the valve within the solenoid. There are several sites that sell replacements for about $70, which is not cheap, but cheaper than buing a new humidifier for $120. Here is one site I found: http://www.iaqsource.com/product.php/honeywell/32001639-002/?product=112783&category=1142
Posted on Nov 20, 2008
I have the same problem and I have 2 of them fairly new. I can't seem to find out what the problem is either.
Posted on Dec 16, 2010
Tips for a great answer:
Dec 14, 2016 | Aprilaire Humidifiers
Oct 28, 2016 | Humidifiers
Oct 24, 2017 | Aprilaire 400 Humidifier
Nov 22, 2011 | Aprilaire 550 Humidifier
Aug 23, 2011 | Aprilaire 550 Humidifier
Dec 01, 2010 | Honeywell HE360A1027 Whole House...
Nov 30, 2010 | Honeywell HE360A1027 Whole House...
Mar 03, 2010 | Aprilaire 600 Humidifier
Dec 29, 2008 | Aprilaire 700 Humidifier
Jul 02, 2008 | Honeywell Power Humidifier: Furnace...
Nov 21, 2017 | Humidifiers
Nov 18, 2017 | Air-O-Swiss Humidifiers
210 people viewed this question
Usually answered in minutes!