Question about Dometic Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It is normal. Your house has to go down a couple more degrees because the heat pump is not working. You can solve this by rewirng you thermostat. Take off the wire that goes to Y and tape off. Then take the wires that are marked w and e or w1 and put the wires to yellow. Do not run ac with it wired like this. If you need more information please post me back
Posted on Nov 29, 2008
Make sure a back draft in the flue is not happening. Wind can blow it out until the flue heats up. The flame sensor may not be close enough to the burner flame. It may be weak and need to be replaced or if its an optical one it may be dirty and not see the flame very well. Its not wasting much gas but it puts extra wear and tear on the gas controls, is noisy, and, as you said, blows cold drafty air. A gas control system that has issues of any kind is not real safe. It needs to get fixed.
Posted on Jan 08, 2009
Tips for a great answer:
Feb 27, 2015 | Heating & Cooling
Dec 20, 2013 | Ruud RGTM10ERBJS 100K BTU 95%...
Mar 20, 2011 | Heating & Cooling
Nov 01, 2009 | Heating & Cooling
Jan 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 22, 2008 | Intertherm P3RA-048K Air Conditioner
Dec 08, 2007 | Heating & Cooling
Aug 05, 2017 | Dometic Heating & Cooling
65 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: