Question about Fujitsu Halcyon ASU9RMLQ Mini Split Wall Mounted Heat Pump Indoor Unit - 9,00
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Fujitsu Heat Pump - problems
I had the same problem. The heater did not work in heating mode. However it was OK in air-conditioning mode. The operation light and the timer light blink twice and then the operation light blinks for 5 times followed by few seconds non blinking, then the cycle repeats again. I have read on the internet that you better unplug the power cord and then plug it again so that the heater re-sets itself. My only problem was that my heater is directly plugged to the power with no visible plug. So I went to the main distribution board and put off the power for about 20 seconds for the whole home. HOORAY!! The heater worked after that.
Posted on Aug 08, 2008
if no cold blowing,evaporator is not working,have you ever heard compressor is running,check this out,no compression of course you dont have cool on evaporator.if the compressor is running check the oprating current,if still have enough freon charge,if not running check thermostat reset setting on the coldest,ifn still not run check overload relay on panel control reset lever to put back compressor to run,check condensing fan if working,if not check also over load protection,this should be done by ac tech nician.have a nice day,dont gorget to rate me, thank's
Posted on Apr 18, 2009
To cancel the timer, press timer on setting until it comes 00.00. Or remove batteries from remote and re fix after few minutes. If still problem persists, check and rectify error code of e-5 as follows:
Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 09, 2011
Tips for a great answer:
Mar 30, 2015 | Fujitsu Heating & Cooling
Jan 01, 2015 | Fujitsu Heating & Cooling
Feb 01, 2014 | Fujitsu Heating & Cooling
Dec 13, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Mar 01, 2010 | Fujitsu Heating & Cooling
Dec 22, 2009 | Fujitsu 24C1 Air Conditioner
Dec 13, 2008 | Fujitsu 18C1 Air Conditioner
Jul 28, 2008 | Fujitsu Heating & Cooling
65 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: