Question about Weather King Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
The power ventor most likely needs to be replaced. But be advised. Goodman normally will not sell parts to anyone but a certified technician. I had to show my masters certificate to buy parts from their outlet. This is a part that has a high rate of failure.
Posted on Dec 01, 2008
If it is making noise, the motor may be ready to give out. The pressure switch could be faulty, but it sounds as if you need to replace the vent motor if you can find a replacement. Otherwise you've got to replace the entire vent.
Posted on Feb 01, 2009
ok this is going to sound funny but it seems as though the polarity is reversed going into your furnance. to correct this proiblem you first need to unplug the unit and where the cord goes into the furnance at that connection disconnect the two wires. Once theses are disconnected switch the wires .All you are doing is reversing the way the electricity flows into the circut board. I would wager that is the problem
Posted on Apr 16, 2009
Your doing well just right. When the call for heat is on the draft motor gets a call from the board to come on. When this happens if no voltage is present at the motor then you ahve abad baord. Replace it.
Posted on Nov 28, 2009
Testimonial: "Very professional with positive feedback. Thanks for the help! "
SOURCE: I have a Rudd furnace
Well first you want to verify that there is gas pressure coming from the connector. Turn off the valve and disconnect the connector. Then turn on the valve for 1 second and back off. You should get plenty of gas flow. Be careful doing this!. Then inspect the opening at the adapter to the control. There is a screen inside there. Make sure the screen is clear(not plugged with pipe dope,lint ect). When the igniter reaches the 2200 degrees you should hear the gas solenoid valve click open releasing gas. If you hear it click and no gas is released you will need to inspect the burner orfices. The orfice has an extremely small hole and there is a posibillity that they are plugged with debris. You will need to use a very small wire(like a tie strap) and insert it into each hole and see if there is anything in the orfice. If you do not hear the gas valve click then it might not be getting the signal it needs due to a weak igniter or flame rectification sensor. Does your furnace have a stand-by pilot that is lit by the hot surface igniter or does the igniter directly light the burner assembly?
Posted on Feb 20, 2010
Tips for a great answer:
Sep 23, 2013 | Rheem Ruud Weather King Corsaire Rheem...
Oct 05, 2012 | FACTORY AC PARTS Furnace Spark Ignitor...
Jan 19, 2011 | Weather King 10AJA3601AH Air Conditioner
Nov 12, 2010 | Weather King 10AJA3001AH Air Conditioner
Jun 01, 2009 | Weather King 10AJA2501AH Air Conditioner
Jan 15, 2009 | Weather King 10AJA3601AH Air Conditioner
Dec 03, 2008 | Heating & Cooling
497 people viewed this question
Usually answered in minutes!