Question about Noritz NORTIZ Outdoor Propane Tankless Water Heater 6.3 GPM
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You are doing everything you can. Your dishwasher probably isn't drawing enough hot water to activate the unit so opening the faucet and flowing more water will activate the unit. Just try to adjust the flow from the faucet to a point it, plus the draw from the dishwasher, will activate the unit. This will come with trial and error as I am sure you have already experienced. Also, open the dishwasher when it does get filled and check the water temperature. You might have the unit set at a low discharge temperature. Do you have a touchpad to control the water temperature adjustment?
Posted on Jun 10, 2009
The 59 code is typically caused by insufficient gas supply to the unit. It can also be caused by obstructed exhaust flow, stuck exhaust damper (located directly on top of the unit's exhaust), insufficient makeup air, or improperly installed venting (i.e. too long or too many elbows).
I would recommend initially checking the incoming gas pressure at the gas connection on the unit. The gas pressure should not drop below 5" water column for a natural gas unit, 8" for a propane system (the unit need to be operating at its maximum output).
Posted on Aug 14, 2009
SOURCE: Water Heater Won't Fire up
There are a few things you'll want to check:
1) make sure you have 120VAC at the outlet
2) measure voltage across the blue/white and black/white wires connected to the gfi (black box inside the unit on the bottom left or right hand side). You should read roughly 100 VAC on both sides. If you don't read voltage on the black/white wire pair, then you gfi is tripped. Look for moisture that might be shorting the gfi.
3) If the GFI checks out ok, you probably have debris clogging your flow sensor
Posted on Aug 15, 2009
SOURCE: Noritz Tankless error code 16
The trick with these hot water heaters is to keep the filter screen clean and flush the system with CLR periodically. Code 11 is ignition error. Is your gas valve turned on?
Posted on Dec 09, 2009
Tips for a great answer:
Sep 12, 2014 | Noritz Commerical Tankless Water Heater...
Oct 01, 2012 | Noritz 13.2 Gallon Residential Tankless...
Apr 08, 2011 | Noritz 7.1 Gpm Propane Lp Gas Tankless Hot...
Oct 29, 2010 | Noritz 7.1 Gpm Propane Lp Gas Tankless Hot...
Mar 06, 2010 | Noritz 6.9 Gallon Residential Direct Vent...
Feb 18, 2010 | Noritz 6.3 Gallon Residential Tankless...
Dec 10, 2009 | Noritz 6.3 Gallon Residential Tankless...
Jan 04, 2009 | Noritz 6.9 Gallon Residential Direct Vent...
82 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: