Question about Kohler 20RES 20 kW L.P./N.G. Genset
Generator indicates UU on display
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Could be the battery voltage. If your battery is not charging properly, the controller on the unit can do some funky things! Exactly how long does it run for? Is this in auto or manual mode?
Posted on Sep 04, 2009
SOURCE: Code UU
Here is the code explained direct from Kohler's manual. I'd disconnect the generator load first.
UU Undervoltage Shutdown occurs if the voltage falls below 80% of the nominal system voltage for more than seconds. Check wiring and connections.
Reduce the load and restart the generator set. —
Check wiring and Check controller configuration, system voltage
and frequency (parameter UU).
Check AC voltage and adjust, if necessary. 5.7
Replace the SCR module and test voltage again. 4.9
Separately excite unit. 5.2
Check stator continuity
See web site for manual :http://www.kohlerpower.com/onlinecatalog/pdf/tp6196.pdf
Posted on Jul 11, 2010
Tips for a great answer:
Jul 11, 2012 | Kohler Electrical Supplies
Aug 09, 2011 | Kohler 12 kW Emergency Power System -...
Jul 13, 2011 | Kohler 12 kW Emergency Power System -...
May 28, 2011 | Kohler 12 kW Emergency Power System -...
Jul 11, 2010 | Kohler 12 kW Emergency Power System -...
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Jan 17, 2009 | Kohler 12 kW Emergency Power System -...
Oct 09, 2008 | Kohler 12 kW Emergency Power System -...
Apr 13, 2018 | Kohler Electrical Supplies
42 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: