Question about Goodman GMS90703BXA Heater
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Your furnace is more than 90% efficient and extracting so much heat from the gas that it condenses instead of blowing out steam. This is good! Figure that for every dollar you spend on fuel, you are getting back 90+ cents back in heat. Compare that to the typical units that only get 70 - 80 cents back in heat.
Yes you should drain your condensate to a proper drain via gravity or a condensation pump. I would recommend you treat the condensate first with a acid neutralizer prior to draining in municipal drains due to it's high content of sulfuric acid. You can purchase these filter type neutralizers on the net or at a good heating wholesaler.
Posted on Feb 12, 2008
SOURCE: goodman gms9090 furnace
Based on your description I would guess that there is a "leak" somewhere between the gas valve and the actual fire. Use soap bubbles to check the connections at the gas valve. Also check the gaskets in the Gas valve the same way. Lastly there may be a cracked or misaligned burner causing the "leak". Best of Luck!
Posted on Jan 29, 2009
Consider a variable output system like a Carrier 58MXA or an American Standard AUX unit. This way the unit will ramp up or down based upon the heat required. These units have two or three Btu outputs so they will modulate to find the right range. Yes they will cost more than the Goodman units but will save you gas dollars for many years to come. Goodman is a good Builders unit but look to fuel economy as prices of fuel increases. Right now your furnace is is using 60 Btu's per square foot. Are you located in Alaska? Here in Vermont if we figure 30 Btu's per square foot, that is one very drafty home. Ask to see their Manual J heat loss. If they say "What" time to move on to another heating contractor.
Posted on Nov 03, 2009
I have a forced air gas furnace and water is leaking from just above the area where the hose is attached. I removed the cover but cannot figure this out. It only leaks (a lot of water) when the furnace is running. Please help asap!!! Tthanks so much, Dianne
Posted on Jan 03, 2010
Tips for a great answer:
Nov 03, 2015 | Coleman Propane Forced Air Heater...
Sep 28, 2015 | Heating & Cooling
Dec 14, 2013 | Honeywell Programmable Thermostat Heater
May 07, 2017 | Coleman Propane Forced Air Heater...
Sep 08, 2011 | Reddy Heater RLP100 Portable Forced Air...
Feb 22, 2010 | Coleman Propane Forced Air Heater...
Jan 04, 2010 | Bosch AquaStar 125FXKIT-LP 125FX Liquid...
Oct 14, 2009 | Dryers
Feb 05, 2009 | Coleman Propane Forced Air Heater...
42 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: