Question about Honeywell HE360A1027 Whole House Humidifier Humidifier
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Honeywell True Steam Humidifier
Yes you will want the out door sensor. The reason why is it is going to read the average temp outside and will adjust what you hum is producing due to the temp outside, that is so you dont cause condensation on your window. You can run it in manuel or auto but i would strongly reccomend to run it in auto.
Posted on Dec 08, 2008
Replace the Valve on the unit. Check the small filter inside of it where the waterline attaches first. If its clear and you have lots of flow from the 1/4" line the replace the valve.
Posted on Jan 19, 2009
you type in on the internet. www.appliancefactory.com
in the search bar type in your model number. it might take a minute to load but you will have 3 pictures that come up. click on any of them and scroll down alittle until you see water tanks. you can order them there.. or if youdon't want to go that route you can always try local hardware stores to see if they have it as well.
Posted on Aug 21, 2009
SOURCE: Honeywell HE260 leaks somewhere
Neither, even if the solenoid or humidistat stick, it should always drain properly. Is the unit mounted on the cold air return duct or the supply plenum? If it's mounted on the supply plenum, the water panel might be getting blown forward and spilling the water. High efficient furnaces also can leak water on the floor if its drain is restricted. If hum. is mounted on return duct make sure drain is clear by blowing through it. On Honeywell hum's I've seen the rubber hose from the solenoid valve to the distributor tray leak too, check the rubber 1/4" hose.
Posted on Jan 21, 2010
SOURCE: Can the humidifier's housing for
Hello Which came first the chicken or the egg?The unit will operate perfectly in the supply OR return as I have installed in both.If there is more room & easy service access put it in there.
Posted on Sep 14, 2010
Tips for a great answer:
Jan 22, 2013 | Humidifiers
Feb 20, 2011 | Honeywell HE360A1027 Whole House...
Dec 15, 2010 | Honeywell HE360A1027 Whole House...
Dec 08, 2010 | Honeywell Humidifiers
Sep 27, 2010 | Honeywell HE440A1005 Humidifier
Sep 14, 2010 | Honeywell Humidifiers
Jan 08, 2010 | Aprilaire 550 Humidifier
Dec 28, 2009 | Honeywell HE260A1010 Whole House...
Jan 17, 2009 | Honeywell HE220A1019 Whole House...
Feb 13, 2007 | Honeywell HE120 Humidifier
Jul 11, 2017 | Honeywell HE360A1027 Whole House...
Jan 09, 2014 | Honeywell HE360A1027 Whole House...
87 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: