Question about Goodman Heating & Cooling
I have a goodman AR48-1
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I have a goodman GMP075-3 that won't turn on. I think it is the pressure switch since I do not have a vent blockage. What is a venter and where can I find it??
Posted on Dec 30, 2008
Your unit has a diagnostic light on the circuit board. You need to look thru a small viewing port to see it. Once you count the number of b links, remove the lower panel and look at the wiring diagram for an error code chart. Then read the following to give you some ideas what to do.
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Dec 01, 2009
Or you need anitfreeze.
Or your thermostat is shot. Both are easy fixes.
Try the antifreeze, first,check and top off.
and if teh problem persists, check and repalce the thermostat.
Posted on Feb 02, 2010
Tips for a great answer:
Jan 25, 2013 | Heating & Cooling
Dec 09, 2012 | Goodman GMS90703BXA Heater
Feb 24, 2011 | Goodman GMS90703BXA Heater
Feb 21, 2011 | Goodman Heating & Cooling
Jan 08, 2010 | Goodman CLQ36AR49 Air Conditioner
Feb 02, 2009 | Goodman CLQ36AR49 Air Conditioner
Jan 30, 2009 | Goodman GMS90703BXA Heater
Jan 09, 2009 | Heating & Cooling
18 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: