# M&K MX-90 Schematics - Home

Posted by Anonymous on

×

my-video-file.mp4

×

## Related Questions:

### I am in need of a schematics for a Ford Louisville 1990 L9000

There are no schematics on the Internet for 90 model. Ford was using books. What are you looking for?

Nov 23, 2014 | Ford Cars & Trucks

### Looking for wiring diagram for 2009 four winds hurricane motorhome

Try the manufacturer first. Most have schematics you can download off the Internet or they will mail it ot you. No luck, google it. 90% of the time you can find one if you are persistent.

Aug 13, 2014 | Four Winds 2009 Hurricane 34U

### 5000 watt inverter schematics circuit

If you have (90) 50w lamps = 4500 watts total. Assuming a 120/240 panel, if you put 1/2 on one "side" of the panel and the other 1/2 on the other "side" of the panel, that would be 2250 watts on each half. The generator should be rated *at least* 125% of the load; 4500w x 1.25 = 5625W. Using a 4500W generator on this load will cause it to overheat and shorten its life as it is running at 100% of capacity all the time..

One half of the panel is 120V to neutral, and the other is 120V to neutral - or 240V between both circuit breaker terminals. Ohms law for DC circuits and purely resistive AC circuits says Volts x Amps = Watts; or Watts / Volts = Amps. So, 2250W / 120V = 18.75A on each pole of a 2 pole circuit breaker that feeds the sub panel. A #12 copper wire is rated for 20 amps; but as per National Electrical Code - must be de-rated to 80% of rating which means it is good up to 16 amps maximum. A #10 copper wire is rated for 30 amps, but it too must be derated to 80%, making it good for 24 amps maximum. So, if you are going to feed a sub panel supplying (90) 50watt lamps, you will need to run a #10/3 copper cable from a two pole 30 amp circuit breaker at the generator to a 120/240 volt "main lug only" sub panel rated for at least 30 amps.

Divide your load evenly across the sub panel - (4) 15 amps circuits via (2) two pole 15 amp circuit breakers on each "side" of the panel if you run (2) 14/3 cables out to the lights - or (4) single pole 15 amp circuit breakers if you run (4) 14/2 cables out to the lights. No circuit breaker terminal should have more than 23 lamps that means you have (2) w/ 22 lamps and (2) with 23 lamps. The circuit w/ 23 lamps will draw 23 lamps x 50w = 1150W. 1150W / 120V = 9.6A. The 22 lamp load will be 22 x 50w = 1100W. 110W / 120V = 9.2A. Which is well within the 12A maximum allowed (after derating as required by code) by a #14 copper wire rated for 15A.

Good luck!

Mar 10, 2014 | Electrical Supplies

### MX 351U SHOWING E7-90 ERROR CODE WHAT THE SOLUTION

This is a PCU PCB Communication error. 9 times out of ten it will reset by simply switching the machine off and then on again. If the problem persists here is the section from the manual that describes the possible causes and remedies.

E7-90
MFP - PCU PWB communication error
Trouble content
Detail
MFP
Cause
PCU PWB connector connection trouble. PCU PWB - MFP PWB connection trouble. PCU PWB trouble.
MFP PWB trouble.
Mother board trouble.
Check & Remedy
Check connection of the PCU PWB, the MFP PWB, and the mother board.
Check the ground.
Replace the PCU PWB.
Replace the MFP PWB. Replace the mother board.
I hope this helps

Good Luck

Jan 14, 2014 | Sharp Office Equipment & Supplies

### Need schematics for Beheringer MX 3242X

Behringer won't give schematics except to their service agencies... I have tried... I usually wind up tracing out enough of the circuit to repair it.

Jan 17, 2010 | Audio Players & Recorders

## Open Questions:

#### Related Topics:

46 people viewed this question

Level 3 Expert

Level 3 Expert