Question about Heating & Cooling
We have an Amana 80SSE Furnace. The furnace came on by itself when the thermostat was turned off. It was blowing cool air and the blower would not turn off. We had to turn it off manually at the switch. We do not have a manual in order to troubleshoot the diagnostic error: 1-flash: system lockout (retries/recycles exceeded).
Not much info to go on, but lets look at a few possibilities. Your thermostat could be turned to the ?Fan On? setting, make sure you put it in the ?Auto? mode. Or it could be bad, or there could be a short in the wiring. Open up the access panel on your furnace. Lets eliminate the thermostat from the equation by disconnecting the red, white and if you have a yellow wire at the furnace. Mark down which wire went where. The furnace will have a door safety switch that will have to be taped temporarily closed to test the furnace. With a short piece of wire (2-3" long), strip off 1/2 inch of the insulation on both ends. Secure one end on the R terminal where you removed the red wire from your thermostat. Take the other end and touch the G terminal on the same electrical board. Your fan will start. Don't worry about an electrical shock, the voltage is only 24 volts. Now with one end still attached to the R terminal, touch the W terminal where the white wire was attached. The furnace will now try to fire up. Hold it there until you see that it did start. If you did this and had success, I would say it was your thermostat or the wire going to it. Last resort would be a bad control board. If you want, you can do test your thermostat wiring by removing the thermostat from it's mounting plate. Put all wires back where they were on the furnace. Make sure the access door is back in place and secure. Take that same jumper and jump across the red and white wires on the mounting plate. Again the furnace should start up. Have a helper jiggle the thermostat wires where accessible when the furnace is running and see if it remains on or shuts off. If everything checks out, replace the thermostat. Good Luck!
Posted on Oct 08, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 15, 2015 | Amana GMH81405DN 140,000 BTU 80% Gas...
Nov 03, 2013 | Heating & Cooling
Nov 04, 2012 | Heating & Cooling
Jan 02, 2010 | Goodman GMS90703BXA Heater
Jun 29, 2009 | Honeywell Programmable Thermostat Heater
Jan 07, 2009 | Heating & Cooling
881 people viewed this question
Usually answered in minutes!