Question about Coleman Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
first off buy yourself a honeywell stat, in my personal opinion lux stats are garbage, I have run into so many that are bad stats !!! but as far as your fan not shuting down, sounds to me like your fan center on your circuit board is bad and will not shut down the fan when needed, you will have to replace the circuit board, as the fan center is a part of the whole of the circuit board, hope that helps
Posted on Jan 20, 2009
SOURCE: i have a coleman/evcon electric
Have you tried to replace pressure switch for the combustion air. If your not sure where to find it if you pull the front panels off follow the flue pipe down to combustion chamber the combustion fan motor is either inside the flue pipe or out side of it not sure on the one you have but you should see two plastic tubes that connect to a barb onto the topside of the fan and one on the bottom they both should go back to the pressure switch. i hope this helps you if you have any more question or if this doesnt fix the problem just reply back to this message . Make sure fan is working when furnace starts up. It should be the first thing that comes on when there is a call for heat
Posted on Jan 21, 2009
Yes, inspect the air intake, exhaust pipe, filter and condensate piping for blockage or moisture. Also check for a hole in the hose that goes from the small exhaust blower to the pressure switch or a bad connection on the switch or control board. You may be able to temporalily jump the switch for diagnostic purposes only.
Posted on Oct 17, 2009
sounds like it is the pressure switch try jumping it out on some models you fool the heater in too working or see if the tubes are blocked , there should be some codes on the front panel or the fan panel
Posted on Apr 27, 2010
Tips for a great answer:
Feb 14, 2014 | Coleman 7990-319p Evcon Gas Furnace...
Jan 08, 2014 | Coleman 7990-319p Evcon Gas Furnace...
May 05, 2011 | Heating & Cooling
Jan 07, 2011 | Coleman Propane Forced Air Heater...
Nov 23, 2010 | Heating & Cooling
Sep 29, 2010 | Coleman Propane Forced Air Heater...
Mar 31, 2009 | Coleman Propane Forced Air Heater...
Jan 16, 2009 | Coleman Propane Forced Air Heater...
77 people viewed this question
Usually answered in minutes!