Question about Coleman York Control Board 03101237000 031-01237-000
The inducer draft motor has to run and develop the proper amount of negative pressure (checked with a monometer) to close the pressure switch before anything else happens. Even if the pressure switch closed and the igniter energized, the gas valve wouldn't function until the flame is proven by a flame rod or rectification. The fan continues to run (inducer draft motor) because it is still trying to light. Call a qualified tech before you kill yourself or others
Posted on Dec 08, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You may have a dirty/rusty burner that is clogged or your gas valve
manifold pressure setting may be too low. Normal manifold pressure
is 3.5 inches water column on natural gas furnaces. ( 1 psig is equivalent to 28 inches water column). Pull and clean burner. Also
check and clean pilot assy. including flame sensor (if present).
Please let me know.
Posted on Oct 24, 2009
Tips for a great answer:
Oct 02, 2015 | Coleman Gas Fired Mobile Home Furnace,...
Feb 16, 2015 | Coleman 7990-319p Evcon Gas Furnace...
Dec 17, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Nov 08, 2012 | Heating & Cooling
Feb 26, 2011 | Heating & Cooling
Jan 21, 2011 | Dayton Gas Furnace Heater
Oct 23, 2010 | Heating & Cooling
Jan 10, 2010 | Dayton Gas Furnace Heater
Nov 15, 2008 | Kitchen Appliances - Others
Jun 13, 2012 | Coleman York Control Board 03101237000...
100 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: