Question about Heating & Cooling
Furnace wait too long to come on and then comes on with big booh and after 5-10 minutes burners and pilot goes off together. I already change the thermocoupler. any advise? Mitchell Manuf. Model 75-AGCF s/n- f1-113
Sounds like the burners need to be removed from the furnace and cleaned thoroughlyto help with gas distribution if these are in-shot burners they look sort of like an air plane, they have a cross over tube on each side of each burner and if that is rusted up the gas will not distribute evenly from one burner to the next if the pilot and burners go off at the same time then it sounds like you may have some flame blow back maybe due to soot build up in the heat exchanger. Overall sounds like your furnace could use a good servicing
Posted on Oct 16, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 30, 2017 | Cozy Heating & Cooling
Nov 29, 2013 | Heating & Cooling
Nov 19, 2012 | Heating & Cooling
Mar 10, 2017 | Heating & Cooling
Nov 08, 2012 | Heating & Cooling
Jan 10, 2010 | Dayton Gas Furnace Heater
Nov 06, 2009 | Cozy (W352E) Heater
Feb 18, 2009 | Water Heaters
Jan 06, 2009 | Heating & Cooling
Nov 13, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
874 people viewed this question
Usually answered in minutes!