Question about Air Conditioners
Furnace wait too long to come on and then comes on with big booh and after 5-10 minutes burners and pilot goes off together. I already change the thermocoupler. any advise? Mitchell Manuf. Model 75-AGCF s/n- f1-113
Sounds like the burners need to be removed from the furnace and cleaned thoroughlyto help with gas distribution if these are in-shot burners they look sort of like an air plane, they have a cross over tube on each side of each burner and if that is rusted up the gas will not distribute evenly from one burner to the next if the pilot and burners go off at the same time then it sounds like you may have some flame blow back maybe due to soot build up in the heat exchanger. Overall sounds like your furnace could use a good servicing
Posted on Oct 16, 2007
Tips for a great answer:
Oct 08, 2012 | Honeywell Icp Heil Tempstar Furnace Spark...
Jan 26, 2011 | Air Conditioners
Nov 06, 2010 | Air Conditioners
Sep 18, 2010 | Coleman Air Conditioners
Nov 28, 2009 | Carrier 38CKC042 Air Conditioner
Jan 06, 2009 | Air Conditioners
Nov 13, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 10, 2008 | Air Conditioners
Oct 22, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 17, 2007 | Air Conditioners
868 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: