Question about Goodman GMS90703BXA Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There is a vacuum sensor on most units tied from the exhaust gas fan to the sensor. Does the unit try to start? If the unit's exhaust fails to pull the switch it will turn off after about 30-45 sec after starting. "IT" thinks it's not exhausting and stops to keep from overheating. Do you have this exhaust fan and rubber hose to sensor? Can you see if that fan is turning on start?
Posted on Nov 10, 2007
No, the board isnt out. The board has a code telling you that its out. Its your flame sensor. You wouldn't have gotten any heat if the gas valve was out. check if that flame sensor goes to another sensor on the same circuit , if it does check that. If it just a one wire sensor make sure its in the right position. If its a one rod flame senor with one wire I would sand it down with sandpaper. if its a two wire senor ohm it out to see if you ger current going through it.
Posted on Oct 16, 2009
In the burner compartment opposite of the ignitor is the flame sensor. seems to be dirty. one screw holds it in. Remove and clean with a wire brush.
Posted on Nov 21, 2009
The problem you have is water in the exhaust pipe.
Check to see if the pipe has sagged anywhere or if there is a trap in the line.
If you hear gurgling then it is definetly water....
Some times can be hard to find, even a pipe 1/4 full will cause problems. They are very sensitive to flue problems.
Make sure that the flue pipe either runs back to the furnace or out to the outside, a continuos slope either way witha high spot in the middle.
Also check the bottom drain of the blower if it has one, have had them plug and trap water also..
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Dec 24, 2009
Tips for a great answer:
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remaing solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Oct 05, 2010 | Goodman GMS90703BXA Heater
Feb 26, 2010 | Goodman Heating & Cooling
Feb 15, 2010 | Intertherm P3RA-048K Air Conditioner
Feb 12, 2010 | Goodman Heating & Cooling
Jan 27, 2010 | Goodman Heating & Cooling
Jan 26, 2010 | Goodman GMS80453ANA Open Flame Mid-Size...
Jan 26, 2010 | Goodman Heating & Cooling
Jan 02, 2010 | Goodman GMS90703BXA Heater
Nov 19, 2009 | Goodman GMS90703BXA Heater
Nov 18, 2009 | Goodman GDS80904BNA Open Flame Heater
183 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: