Question about Heating & Cooling
Question is there a water line hooked up to the furnace?
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
NO BECAUSE THE BOARD IS TELLING THE FANS TO STARTARE THE CONTACTS FUSED TOGETHER OR STUCK IN THE CLOSED POSISTION CHECK THIS FIRST
Posted on Aug 10, 2009
Hi, If you are trying to get gas to the furnace, you will have to tee off the water heater with 1/2" black iron gas pipe up to the unit. This is code. At the end if the run you will need to install a gas shut off valve and reduce to 3/8" flare to connect a 36" flex to furnace. I have 2 men who do just this, run gas lines all day. That is how it is done. Hard work. We use a rigid portable pipe machine to do this. Best of luck,
Posted on Dec 21, 2009
Testimonial: "it helps to know you're in the right direction. Makes the smaller jobs not normally done, easier."
PRSSURE, DRAFT SAFGUARD, AUX-LIMIT SWITCH(WHEN USED)OR BLOCKED VENT
SWITCH(WHEN USED) DID NOT CLOSE OR REOPENED (DOWNFLOWONLY)
If open longer than five minutes, inducer shuts off for 15 minutes
* proper vent sizing
* defective inducer motor
* restricted vent
* excessive wind
* low inducer voltage(115VAC)
* defective blower motor or capacitor
* defective pressure switch
* inadequate combusstion air supply
* disconnected or obstructed pressure tubing
If it opens after trial for ignition period, blower will come on for
90 sec. recycle delay.
Check your air filter for blockage, check pressure switch for a buildup of moisture. Make sure your inducer motor is turning and creating a vacuum to the pressure switch. Make sure all venting is clear and free of water or debris. Make sure there is no water in inducer motor and all drains are draining.
Posted on Jan 28, 2010
You have not mentioned if the vent pipe has any anti-vibration mounts or not. If not, use rubber mounts to suspend the vent. It may be transmitting your noise.
Posted on Mar 11, 2010
these codes are on the inside panel of the front cover of the furnace. lift off and look inside.there should be a code explain chart on the panel by the light. this panel will need to be replace correctly for the furnace to work as there is a door switch.
Posted on Feb 01, 2011
Tips for a great answer:
Jan 17, 2014 | Heating & Cooling
Sep 03, 2013 | Bryant 92 Afue Gas Furnace Legacy359aav...
Jan 31, 2011 | Heating & Cooling
Oct 23, 2010 | Heating & Cooling
Jan 28, 2010 | Heating & Cooling
Dec 20, 2009 | Heating & Cooling
Aug 18, 2009 | Bryant Heating & Cooling
Jul 04, 2009 | Goodman CLJ30AR32 Air Conditioner
131 people viewed this question
Usually answered in minutes!