Question about Hardware & Accessories
Need manual for circuits
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Wiring will appear on side of timer.
Test the timer with multimeter to see which terminals are connected. When timer has no power, then Com and NC terminals will have continuity.
H5CX-A Timer has 11 screw terminal connections and timer is rated 100V to 250Volt AC 50-60Hz.
Input is power IN > this is the 100V to 250Volts coming from breaker box or transformer. For example input terminals might be labeled A and B.
This will give power to timer, but remainder of screw terminals have no power.
To put power to relay terminals, jumper the power from Input terminal A to COM terminal.
For example Com terminals might be 7 and 9.
So jumper Hot wire from Terminal A to terminal 7.
This action will put hot on Com terminal 7, but also give power to the NC terminal.
For example the NC terminals might be 1 and 3.
So when timer is OFF, the NC terminal has power.
Then when timer turns ON, the NC terminal no longer has power, but the NO terminals are Hot.
NO terminals might be 4 and 6, and these terminals turn on-and-off when timer turns on--and-off
Open following link to help with Omron 11-pin wiring:
Posted on Jun 25, 2012
I see your comment to ignore:
To protect timer, read following:
1) Max load on this timer is 5 amp at 240volts
2) If load exceeds 5 amps, then use timer to control contactor.
Here is crude drawing showing basic wiring for pin timer controlling heavy amp load.
3) If amp rating on incoming wires exceeds 5 amp, for example is circuit breaker feeding circuit is 20-30 amps etc, then protect wires to timer using busman in-line fuseholder with fast-acting 5 amp cartridge fuse.
Posted on Dec 04, 2012
Tips for a great answer:
Jul 06, 2014 | Omron H3CR-H8L-AC100120M Solid State Power...
Jan 31, 2013 | Connecticut Electric Electrical Supplies
Dec 04, 2012 | Hardware & Accessories
Dec 03, 2012 | Omron Healthcare Omron H3y-4 5 Second...
Nov 22, 2012 | Omron H5CX A AC100-240 Multifunction...
Sep 07, 2012 | Hardware & Accessories
Sep 07, 2012 | Amperite Dayton Solid State Timer On Delay...
Aug 15, 2011 | Amperite Dayton Solid State Timer On Delay...
Jun 23, 2011 | Intermatic ET70415CR Energy Controls - ETS...
May 18, 2018 | Hardware & Accessories
39 people viewed this question
Usually answered in minutes!