Question about Flow Pool & Spa
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: No Heat from Spa
Heater contactors "buzzing": Do you mean normal buzzing or extra loud buzzing? Loud buzzing or chattering can be caused by low voltage to a contactor. If normal sounds, then probably the relays on the contactors is working, but the contacts may be stuck, or burned enough so as not to make contact. First, get a voltmeter and check for 240 volts AC at the heater contactor terminals. If the voltage is low, most likely you need to check the contactors further. Check for dirty contacts, clean if needed. If the contacts are not moving when energized, then you will probably need to replace one or both of the contactors.
Posted on Jan 18, 2009
I had a similar problem and it turned out to be the solder connections on the control module. The connector that is soldered to this board (comes from the gas valve) needed to be re-soldered.
Posted on Jun 14, 2009
Your EO4 message tells you you have a fan problem. So ether your fan is diying wich you would hear or you have a bad presure sensor in your exaust. A new fan is a little pricey but the sensor is reasonable for heater parts. I can't be sure but I believe it ether screws onto or into your exaust and it just plugs on to your control board. If your sensor is going bad their is a reason and this should be addressed. It should be in your by-pass or your gas pressure. But as far as a new heater, not untill you have water coming from the cabnit. It is sometimes easer to sell new than keep up with new, Good luck let me know how you do.
Posted on Dec 03, 2009
One of your limits is not working or not wired up. An easy way to check the limits - Water pressure switch, Hi limits, air pressure switch all of which have 2 wires going to them. Unplug one item and connect the 2 wires together ( paper clip works fine ) Then retest, if problem does not go away remove paper clip and reconnect wires and move to the next limit. The limits are located in the black plastic header. Always make sure water is flowing through the heater at all times while checking the limits.
Posted on Mar 01, 2010
Tips for a great answer:
Jun 07, 2015 | Pool & Spa
Sep 15, 2014 | Pool & Spa
Oct 03, 2013 | Pool & Spa
Oct 25, 2012 | Balboa Instruments Duplex Digital Panel 2...
Apr 11, 2012 | Laing Thermotech Water Heaters
Feb 27, 2011 | Laing Thermotech Laing Circulation Spa...
Nov 18, 2010 | Laing Thermotech Laing Circulation Spa...
Jan 29, 2010 | Jacuzzi RapidHeat In-Line Heater U395000 [...
101 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: