Question about Heating & Cooling
From hanging around this site i've read that the thermocouple needs a sanding to generate enough power to give feedback that the flame is working ok
Posted on Oct 22, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Pilot light lit but no heat
the pilot's millivolt generator may be at fault. if you have a meter that is capable of measuring a very small DC voltage, connect it up to the very end of the thermocouple and the copper cappillary. the thermocouple has a welded bead at the very end inside that generates a small DC voltage. Same principle of a J-K thermocouple. Iron constintan - two dissimiller metals where joined together produce a voltage when heated. the thermocouple actuates a millivolt electromagnet inside the valve to keep the valve pellet open. no voltage there it won't actuate the electromagnet.
Posted on Oct 15, 2007
SOURCE: yellow pilot on heater
posted on May 06, 2008
Rating: 90%, 19 votes
All it needs is a good blow out with compressed air. They tend to carbon up in the pilot light area. You will probably also find it is very dusty inside. Easiest way to clean the carbon out is to remove the hose at the heater and with compressed air blow through the fitting where you have removed the hose. Make sure you hold down the start button so the air can get through to the pilot light and jets. Don't connect the electricity for the fan when you do this. If you can get to the top of the pilot light it may help to give that a blow out too.
To clean it out internally you only need to remove the front panelling. Just follow the screw configurations *** you go. I asm not familiar with that type of heater so thats about the best I can do. Regards Bryan
Posted on May 07, 2008
The problem is likely to be either the thermal-couple (easily replaced) or a clogged gas orrifice. The clogged orrifice would require a bit more know-how then the thermal-couple and with gas appliances it would be best to hire someone who knows what they are doing.
Posted on Mar 21, 2009
Tips for a great answer:
Mar 25, 2015 | Heating & Cooling
Mar 05, 2015 | World Heating & Cooling
Dec 08, 2014 | Water Water Heaters
Nov 09, 2014 | Heating & Cooling
Nov 28, 2013 | Empire Direct Vent Wall Furnace;...
Mar 21, 2012 | Water Heaters
Jun 13, 2011 | Reliance Natural Gas Water Heater Control
Feb 21, 2010 | Montgomery Ward (223600UP) Heater
Mar 29, 2009 | Desa International GWN10T Wall Mounted...
Mar 23, 2009 | Coleman Propane Forced Air Heater...
28 people viewed this question
Usually answered in minutes!