Question about Kohler 12 kW Emergency Power System - 12RES-L
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If the succession is 3-5 sec crank - 3-10 sec pause, it is OK, but the cranking is not successful (the reason should be investigated).
If the succession is more rapid 1 - 2 sec you may have bad PCB control.
Posted on Jun 14, 2010
check your load wires there probaly reversed. I had the same problem friday. The week before the electrican wired it. did the same cc1 then oc. had a generator company come out it was the wireing. my load and netural were reversed.
Posted on Sep 20, 2010
SOURCE: Kohler 12 RES - Unit fails to start occasionally. Attempting a manual start by placing switch in run position, cause a loud click, but no cranking. The panel says CC. This morning I put a jump star
I finally solved the intermittant starting problem on my Kohler 12 RES by replacing the strater and the starter relay. I was also experiencing the occassional OC indication, red blinking LEDs on the ATS, and intermittent non-starts during the weekly exercises. The problem happened during power outages a couple times also. If I flipped the start switch between auto and run quickly the generator would occasionally start. Once started, the generator runs fine. I ordered a new starter, which included the starter solenoid. By the way, don't worry about the genuine part thing..the old starter was a Delco made overseas. I ordered a new starter online for $85 (6744N) and it was indentical to the genuine Kohler starter. Replaced the starter and it improved the problem but did not totally solve the intermittent starting. Ordered the starter relay (GM49746) replaced it and the problem is solved.
Posted on Jun 23, 2012
Tips for a great answer:
Jan 06, 2014 | Kohler 12 kW Emergency Power System -...
Sep 14, 2011 | Kohler 12 kW Emergency Power System -...
Sep 01, 2011 | Kohler 12 kW Emergency Power System -...
Dec 01, 2010 | Kohler 12 kW Emergency Power System -...
Jun 03, 2010 | Kohler 12 kW Emergency Power System -...
Apr 07, 2010 | Kohler 12 kW Emergency Power System -...
Feb 04, 2010 | Kohler 12 kW Emergency Power System -...
Jan 25, 2010 | Kohler 12 kW Emergency Power System -...
220 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: