Question about Water Heaters
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Most likely only one of the pipes is leaking but weaping enough to cover the top and indented places near both inlet and outlet. This leak has most likely penetrated all the insulation and is a problem throughout the tank wrap insulation...If you are able to blow air continuously long enough to determine which connection is leaking then fix it. It will likely to take quite a while to dry out all the insulation if the water has migrated down into the tank wrap... If you determine that the insulation is waterlogged, you may be able to drill several small holes in the external cover.
Posted on Jan 06, 2009
1) Shut the breaker off to it at the panel. 2) Hook a hose up to it (the bottom has a drain). 3) Close the valve to the water heater (on the cold water supply). 4) Open drain on the bottom of water heater. 5) Open the relief valve to allow air into the tank (it won't drain otherwise - think if you put your finger on one end of a straw - the liquid stays in until you let go). Why are you draining it by the way?
Posted on Jan 31, 2010
If I understand correctly, the pilot light is not staying lit.
You light the pilot and water in the tank reaches temperature.
Once hot water is gone, then pilot light has to be lit again.
Gas pressure is good, and gas is flowing.
Thermostat is working at high end because it cuts off heating.
Vent is working because tank heats up.
Air intake is working.
Gas control thermostat might not be reading low temperature. Replace gas control valve.
Pilot tube might be dirty. Clean burner parts and combustion chamber, and air intake, and vent.
Backdraft might be blowing out pilot. Check for constant updraft by running water heater 5 minutes, and then light match under vent hood and see if smoke goes up.
Very hot air can put out pilot, especially when water heater located in attic. Add ventilation.
Improper vent might have water dripping back down into combustion chamber and putting out pilot light and rusting out the parts. Inspect for rusted parts and water.
Posted on Aug 10, 2011
Tips for a great answer:
Oct 21, 2013 | Reliance Natural Gas Water Heater Control
Mar 29, 2013 | RELIANCE ELECTRIC WATER HEATER
Jan 13, 2013 | RELIANCE ELECTRIC WATER HEATER
Oct 25, 2012 | RELIANCE ELECTRIC WATER HEATER
Aug 25, 2011 | RELIANCE ELECTRIC WATER HEATER
Jul 31, 2011 | Reliance Natural Gas Water Heater Control
Jul 24, 2011 | RELIANCE ELECTRIC WATER HEATER
Dec 05, 2010 | RTO Atwood DSI-RV Water Heater-6 Gallon
May 24, 2010 | RELIANCE ELECTRIC WATER HEATER
Jan 25, 2010 | Reliance Water Heater #6-30-DORT 30GAL...
181 people viewed this question
Usually answered in minutes!