Question about Fujitsu "AOU12RLS 12,000 BTU Cool/16,000 BTU Heat Halcyon Ductless Mi"
Need to check and make sure the condensing fan ( outdoor unit fan) wires are not hitting the fan blade, it could also be that the fan blade needs to be balanced.
Posted on Oct 22, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
E5 indicates excessive temp. of the outside coil if on cooling, OR excessive temp of the inside coil in
heat mode. On cooling, the E5 will appear if the outside coil temp exceeds 68C. This is an indication
of condenser airflow reduced or non-existent. Using the procedure described above it is possible to
watch the condenser coil temp using the Temp down button and Medium fan speed combination to
display this temp. NB: if fans etc seem to be OK then measure thermistor resistance and refer to table
12. In case the problem is thermistor calibration.
Action: If unit is in cooling mode, examine both condenser fans are running. If
one is running then suspect a faulty motor. If both fans not running then
on units up to serial No. IBSA 01175, investigate the fan speed control
card located in enclosure on the LHS See fig 6.
If this checks OK then investigate main control card.
Fig 1, 2 or 3. Units with serial No's IBSA01176 and
onward are multi speed tapped wound motors not requiring a speed
control card. If both motors inoperative then suspect main control card
Aug 15, 2016 | Heating & Cooling
Sep 19, 2015 | General Electric AHH40LH Dehumidifier
Nov 07, 2014 | Fujitsu 12RLS Wall Ductless Air...
Jul 13, 2012 | 1993 Mitsubishi 3000GT
May 28, 2012 | Panasonic Th-50pe700u TV
Sep 24, 2011 | 2001 Jaguar S-Type
Mar 30, 2011 | 2009 Ford Flex
Jun 26, 2008 | Goodman CKL60AR60 Air Conditioner
Aug 26, 2007 | Ruud UAKA037 Air Conditioner
Sep 20, 2017 | Heating & Cooling
89 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: