Question about Sharp Refrigerators
Replaced Relay & Overload protector. after replacing same problem it could be compressor defective.
Posted on Jan 04, 2016
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
you need to replace the start components on the compressor, theres a relay that mounts on to the compressor that takes out the start winding after it starts the compressor up. You can also try whats called a three in one to try to start up the unit. Good Luck.
Posted on Mar 28, 2009
Either the start relay mounted on the compressor is hanging up and the protective overload is shutting the compressor down, or the compressor itself has an internal problem.
You can remove the relay from the compressor pins and take it to an appliance parts house for testing.
They will be happy to check it or you. If defective, replace. If it checks out O.K. then you have an internal problem with the compressor and it will take a qualified tech to sort it out.
Posted on Apr 02, 2010
SOURCE: how do change the
Unplug the refrigerator. Remove the lamp cover by lifting up at the bottom of the cover. Then unscrew the old bulb and replace with an identical appliance bulb (Base E12, 240V, MAX 15W, T-20). This bulb is at the top center of the fridge.
The manual is available here: http://safemanuals.com/414159.php?ID=1286636&k=3942fa3f433aa4c53ff8bcb7d07ae8e8&q=SHARP%20SJ-P43N/P47N/43N/47N . You will need to review the fridge or enter a code to download the PDF. The light replacement instructions are on page 6.
I hope this helps.
Posted on Feb 25, 2011
Tips for a great answer:
Dec 04, 2012 | Kenmore 7.5 cu. ft. / 212 liter Upright...
Jul 12, 2010 | 1994 Chevrolet Sportvan G30
Sep 02, 2009 | Electrolux Icon 22.6 cu. ft. Counter-Depth...
Mar 11, 2009 | Refrigerators
Feb 01, 2009 | Heating & Cooling
Jun 22, 2008 | Coleman Mach III Air Conditioner
Oct 26, 2007 | Heating & Cooling
114 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: