Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
The first thing to look at is the flame sense rod.
Shut off power to the furnace, remove, clean sensor with steel wool or sandpaper then reinstall the sensor. Reapply power and it should run properly.
Posted on Jan 10, 2009
You can try the 4 amp fuse thats on the inside of the unit, on the board, if you feel confident that there is 120v going to the unit. Having issues with the board can be a bad sign and not knowing what they have already done to it kinda leaves me in the dark, but you can try that and if the fuse blows again, you have other problems going on that they will have to trouble-shoot. The unit is still under the 5 year warranty so it might be best to try and get another board all together, you should only have to pay labor cost. It could be the transformer too, you can check it with a meter to see if your getting the 120v going in and 24v going out if capable. Hope this helps some and good luck!
Posted on Jul 14, 2010
Tips for a great answer:
Dec 16, 2014 | Goodman Manufacturing Goodman Gas Furnace...
Nov 03, 2014 | Goodman Manufacturing Goodman GMH81205DX...
Oct 20, 2013 | Heating & Cooling
Oct 28, 2011 | Goodman GMS90703BXA Heater
Feb 04, 2011 | Goodman GMS90703BXA Heater
Jan 25, 2010 | Goodman Heating & Cooling
Dec 11, 2009 | Goodman Heating & Cooling
Oct 10, 2009 | Heating & Cooling
Jan 14, 2009 | Goodman GMS90703BXA Heater
Jan 10, 2009 | Goodman GMS90703BXA Heater
67 people viewed this question
Usually answered in minutes!