Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Try putting your fan in the on not auto position and see if your outdoor condensing unit cycles on and off. If it does you might have a defective time delay relay to blower. If not your contactor might be stuck or your thermostat could be defective.
Posted on Jun 01, 2008
SOURCE: I have a Amana air
This sounds like your condenser contactor, contacts are stuck. They weld together if an ant or other debree get between the contacts. Turn off the electric breaker to the outdoor unit as if the outdoor unit runs without the indoor unit running you may damage your outdoor unit compressor.
I would suggest you call a service company. The part should run retail @ 30 to 40 dollars then the service call charge. This repair should take less than 1/2 hour.
Posted on Oct 18, 2008
SOURCE: Amana Gas furnace, Air Command
Buy a new ignitor here; The Ignitor Store. Or talk an Amana dealer/Contractor to sell you one. They can range from 15 to 35 bucks! Depending on their mark-up. Give them your model number, and or ignitor part number. Their simple to change out, good luck, please contact if you have any questions.
Posted on Dec 02, 2008
Sounds as though the power cord reset switch might be bad and need to be replaced. If not, then there is a short somewhere in the system. Do an ohms test on the switch to determine if it is bad.
Posted on Mar 17, 2009
water should never reach the nipple for the pressure switch tubing on the IDM. Check the entire condensate drain system for obstructions. Verify water makes it from the furnace location to the outside drain. Flush p-traps and any anti-siphon devices thoroughly.
Posted on Apr 07, 2009
Tips for a great answer:
Mar 14, 2018 | Cars & Trucks
Dec 06, 2016 | Heating & Cooling
Sep 17, 2017 | Amana Heating & Cooling
Mar 14, 2010 | Heating & Cooling
Jun 25, 2009 | Dehumidifiers
Jun 25, 2009 | Heating & Cooling
Feb 06, 2009 | Carrier Heating & Cooling
Nov 15, 2008 | Amana Heating & Cooling
Sep 06, 2008 | Amana Heating & Cooling
33 people viewed this question
Usually answered in minutes!