Question about Haier 2.0 Ton Multi-position Air Handler Hb2400vd2m20 Air Conditioner
Honeywell 5000, 8000, 8000 iaq, prestige, round dial analog, digital Honeywell redlink. 1 heat 1 cool thermostat 3 heat 2 cool thermostat. does the stat u have do conventional a/c and heat pump. red wire is hot wire 24 volts not heating its your 24 volt control power. this will be r on your board and t-stat and red wire. y is for cooling mode and is yellow and will be noted y on both board and t stat. green is fan on the indoor furnace and will be g on board and t-stat and the wire is green. blue is the common side of the transformer labeled b on both board and t-stat. I did not see brown on your schematic I looked up I seen orange which is your reversing valve wire for the heat pump whether its calling for cooling or heat this is what changes the flow of Freon to make it to the indoor coil as warm Freon or cold when called for in heat or cool. the thermostat if a vision pro 8000 needs to be programmed in the installer mode which if this is the t-stat u have u need to read through the heat pump section. the green hooked to the orange doesn't look right on the print but that's the breakdown. http://www.manualslib.com/manual/277678/Haier-Hb2400vd2m20.html?page=11#manual heres your schematic
Posted on Oct 20, 2013
Testimonial: "well I hooked it up like you said before I posted this and the stat does not come on.. so I thought maybe it had something to do with orange and green being together that wasn't it either, I am getting 24volts but nothing is showing on stat its a digital and tried another stat and still no change. so I was wondering maybe it came with a bad board.. what are your thoughts?"
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Got to use the 75 amp rating. otherwise you risk buring up your wires from over amping, fire, blowing fuses continiously, and breaker tripping. Not to mention possible damage to unit.
Posted on Jan 27, 2010
Testimonial: "I thought so...thank you"
SOURCE: The wiring neutral (white) and
Well in the UK & Europe, AUS & NZ, the black wire is neutral.
Any other colored wire (except green) is know as live/active/hot.
Use a tester, one touching the metal casing or earth & the other to see if the wire is hot/live/active.
Posted on Jun 08, 2011
Tips for a great answer:
Mar 05, 2015 | Honeywell TH8320R1003 VisionPRO 8000 w/...
Jul 25, 2012 | Heating & Cooling
Sep 13, 2011 | Honeywell Heat/Cool Thermostat
Jun 25, 2011 | Honeywell Heat/Cool Thermostat
Sep 18, 2010 | Honeywell Programmable Thermostat Heater
Aug 05, 2010 | Honeywell Heating & Cooling
May 09, 2010 | Honeywell Programmable Thermostat Heater
Mar 23, 2010 | Heating & Cooling
Jun 01, 2009 | Honeywell Programmable Thermostat Heater
Dec 02, 2007 | Heating & Cooling
122 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: