Question about Heating & Cooling
Make sure you give it time. The fan has a time delay in heat mode and doesn't come on until it warms up first.
Posted on Oct 28, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Do you have gas or electric heat. If you have gas then you do not have a heat pump. You should in most cases have a red,yellow, white, and green wires coming to the thermostat. R should go to rc/rh G should go to green Y should go to Y and w should go to W. Also the switches on back should be switched to non heat pump and gas rather than electric. Hope this helps.
Posted on Feb 16, 2009
The reversing valve coil may be bad or no power to it during cool. Most heatpumps are set to have the coil of the reversing valve energize in the cool mode. The heating mode is the fail safe mode if the rev valve fails to energize. Check this and let me know.
Posted on Jun 20, 2009
No, you probably have a bad evaporative fan motor, capacitor or switching. It usually takes a Pro 1/2 hour to track down such a problem with good training.
Posted on Jul 09, 2009
If you have changed the motor, I assume that the RPM is the same as the motor you have removed.?
Check the rotation of the new motor, if you have it turning in the wrong direction, it does not matter how fast it turns, it will not send enough air across the evaporator and condenser coils.
Also, if you have changed the motor, you should also change the run capacitor for the power motor.
Hope this info has helped you.
Posted on Oct 08, 2009
mcdevito75, Needs service either a chrge of freon or the need for a new thermostat and That is what it sounds like to me, (the compressor could be bad also, the buzzing sound) hope not expensive repair.
Posted on Jun 24, 2010
Tips for a great answer:
Nov 09, 2014 | Heating & Cooling
Jan 01, 2014 | Intertherm Heating & Cooling
Oct 13, 2013 | Heating & Cooling
Sep 24, 2012 | 1999 Pontiac Grand Am GT
May 28, 2010 | Honeywell Electronic Programmable...
Jul 25, 2009 | 2006 Chevrolet Suburban
Jan 11, 2009 | 1998 Ford Ranger SuperCab
Aug 10, 2008 | 1997 Pontiac Bonneville
27 people viewed this question
Usually answered in minutes!