Question about Fasco ICP Heil Tempstar Furnace Inducer Motor 1011409 HQ1011409FA 1011412 HQ1011412FA
The bearings in the motor is getting hot and locking up. Need new inducer motor.
Posted on Oct 20, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 15, 2017 | Water Heaters
Feb 09, 2013 | Heating & Cooling
Dec 26, 2010 | Goodman CACF048B2A Air Conditioner
Dec 15, 2010 | Heating & Cooling
Mar 12, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 18, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 20, 2009 | Whirlpool Dryers
May 30, 2009 | Dometic Rooftop RV Air Conditioner
Mar 11, 2009 | Heating & Cooling
Not having a make or model number, I can only give you generic information. However if you add more info, others and myself can give you a better diagnosis.
In order for a furnace to start that has an inducer motor, the thermostat must call for heat. Then the circuit board will flash rapidly. There should be power from the board up to the inducer motor. If there is too much resistance, the blower motor or pressure switch(s) will shut down the unit. I would suggest that if you can spin the inducer motor by hand, check for resistance. It may be frozen up or there may be water in the housing not allowing the blower to turn. Check for a plugged water drain at the bottom of the blower housing and make sure it drains. If the inducer blower does not even try to start, you will need to check for voltage from the circuit board. Not knowing for what you have for a model, I am unable to tell you if you should be checking for AC or DC voltage.
Get back to us as soon as you can with more info.
Thank you for your patience.
Oct 18, 2007 | Heating & Cooling
142 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: