Question about LG LW1200ER Air Conditioner
What is the Brand of your Air Conditioner? An LG LW1200ER is a window unit....I'm a bit confused.
Posted on Oct 18, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
These new furnaces are trouble. Ive been in the htg trade for 25 yrs. The fan is running because they are now controlled by a timer instead of a temperature control. Rather than sensing a preset temperature and turning on the fan, it comes on by a preset time. Couple of things, does either of the doors have an inspection window? most newer furnaces have what is called a smart board. The board will flash a trouble code. ie: 1 long 2 short etc. #1 turn your thermostat to off, youll need 2 people for this! Go to the furnace, If it has the above mentioned inspection window ( usually about 2" round) while peering through the window have someone turn the thermostat to about 80 degrees. Let the furnace cycle and see if it flashes a code. If it does the codes are usually on the bottom door, May be on the inside. The most common cause is either a bad transformer, bad hot surface ignitor or pressure switch failure. Further questions feel free to ask. Steve
Posted on Dec 21, 2008
I would try to check your return air first, making sure there is no blockage and that your air filters are clean. It almost sounds like when you take the cover off, you are pulling enough air into the system for it to run, but as soon as you close it off, it's not getting enough air flow, therefore, tripping a limit switch inside the furnace. Most furnaces will also have the codes for the flashing lights and what they mean on the inside of the door covers.
Posted on Feb 03, 2010
Tips for a great answer:
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Feb 10, 2011 | Heating & Cooling
Oct 23, 2010 | Ruud Heating & Cooling
Feb 02, 2010 | LG LW1200ER Air Conditioner
Feb 05, 2009 | Ruud UBHC Air Conditioner
Sep 15, 2008 | Ruud UBHC Air Conditioner
Mar 05, 2008 | Ruud UBHC Air Conditioner
Jan 19, 2008 | Ruud UBHC Air Conditioner
45 people viewed this question
Usually answered in minutes!