Question about Heating & Cooling
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Furnace will not heat.
Most of the Lennox G-16s that I have repaired were having problems with the gray Penn-Johnson Piggyback igniton control module.
This is best repaired by replacing the spark module. Sometimes it may be neccesary to replace the gas valve also. Lennox updated to a ROBERTSHAW ignition system. Honeywell can also be used.
Also check that there is no water in the pressure switch or tube.
Hope this helps.
Posted on Jan 15, 2009
You may need to replace the Thermocoupler. It screws into the gas regulator and the sensor end is set in the flame of the pilot light. You can get one at any appliance parts store. The Thermocoupler simply feels the heat of the pilot light and sends a very small amount of voltage to the gas switch that opens when your thermostat calls for heat. If the pilot light isnt lit, no voltage from the sensor and no gas can be released by the regulator.
Anyone can replace one. Just find the tip that sits in the the pilot flame when you try to ignite the pilot light. Follow it down to the regulator and unscrew it. There is no gas involved. It is Ultra Low Voltage. No danger.
Be sure to turn off the power to the unit before you begin removal. Take it to the parts store along with your furnace brand and model number. If you see any identifiers on the regulator, note them and take them with. When you replace it be sure to have the sensor end up in the flame of the pilot.
Posted on Sep 29, 2009
SOURCE: lennox intermitent flame problem
Yes the flame sensor is not allowing the ignitor to start, you will need to remove the flame sensor, and clean the black carbon build up from the stem of the flame sensor, replace the flame sensor and turn the furnance back on, this will correct the problem.
Posted on Dec 14, 2009
While holding down the control knob for the pilot, you either have to use the pilot ignitor or match light the pilot. Then old the knob in for 60 seconds, before releasing it. If the pilot remains lit, turn the control knob to ON. If the pilot does not remain lit, the Thermocouple or Thermopile may need to be replaced.
Hope this helps you to solve the problem.
Posted on Mar 23, 2011
Testimonial: "Thank you!"
Tips for a great answer:
May 03, 2014 | Emerson Lennox Ducane Armstrong Furnace...
Mar 09, 2014 | Heating & Cooling
Nov 19, 2012 | Heating & Cooling
Mar 23, 2011 | Heating & Cooling
Oct 29, 2010 | Heating & Cooling
Sep 29, 2009 | Heating & Cooling
Jan 13, 2009 | Honeywell Electronic Programmable...
53 people viewed this question
Usually answered in minutes!