Question about Generac 40 Kw Natural Gas/propane Generator
Check the comprssion, if you are sure you have a spark and gas. Is the fuel been delivered to the cylinders? Check the fuel solenoid for power, if power is present the demand gas regulator maybe gummed up. LP companies put a waxy lubricant in the gas and over time this can build up and harden in regulators. Also during crank observe the throttle is it going open as it should? if not suspect a control issue
Posted on Nov 17, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Generac generator remote start
si tiene transfer automatico solo poner un swicht en hilo 1N para cortar senal de entrada al generador del utility power que sensa la presencia de voltage en caso de falta arranca el generador en forma de prueba
Posted on Jun 20, 2010
If it was installed only five months ago, it should still be under warranty. Call Home Depot and have them send out a repair person.
Posted on Jul 01, 2009
Sounds like the electritian wired something wrong. Control wiring for that generator should be:
N1 and N2 = 240 vac utility input
Wire 0 = ground
Wire 194 (15B) = + battery
wire 23 = transfer signal
Posted on Oct 30, 2009
Overcrank means that it tried to start and couldn't. It will go through 5 crank cycles and then stop with this alarm. Switch to off, hit enter to clear fault and then try to start in manual. Check to make sure you have fuel and pressure is 11 to 14 in WC.
Posted on Sep 21, 2012
Tips for a great answer:
Feb 08, 2016 | Generac Guardian Air-Cooled Standby...
Dec 12, 2015 | Generac GUARDIAN Standby Generator 10 kW/9...
Jan 07, 2015 | Generac Electrical Supplies
Aug 17, 2014 | Generac Guardian 8kw Standby Generator
Apr 02, 2012 | Generac Power Systems Generac 5793 Ix 2000...
Jul 01, 2009 | Generac 13,000 Watt / 13,000 Watt Home...
Jun 27, 2009 | Generac Guardian 200 Amp Transfer Switch...
Mar 29, 2009 | Generac 13,000 Watt / 13,000 Watt Home...
134 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: