Question about Heating & Cooling
I have a Williams gas wall furnace Model No. 3509622 and I tried to replace the thermocupling and realized it would be easier to replace the entire Pilot/Generator Assembly which is one piece. Where do I get one and does it show a picture of it. It says my part number is P501617.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: How to reset vent safety switch
the reset is at the top left side of the furnace. take the cover off n press the red button. the switch could be failing but CHECK drafting through the furnace. hold a flame at the top of the furnace n make sure its pulling inward. u could have a blocked vent pipe or vent cap which will cause excessive heat n tip the safety switch. good luck!
Posted on Nov 24, 2009
Assuming the pilot is clean and sharp. Before replacing the valve, clean any spade connections, those going up to the spill switch in particular. Clean and tighten all 4 connections. Good luck.
Posted on Jan 11, 2010
Hi, this heater doesn't have a thermocouple, it uses a pilot generator which is more reliable so I doubt you need to change it out. First thing to check is that you have a clean "sharp" blue pilot, you should be able to hear it quietly roar. If it is yellow and appears "soft", the pilot need to be cleaned. The easiest way is to use a straw or tubing of some sort to blow into the pilot, gently tapping the pilot assembly. That should clean it up and heat the pilot generator properly. Tighten the the screw terminals at the control valve to assure good electrical connections and last but not least turn off the thermostat until you get a standing pilot. Good luck and stay warm.
Posted on Jan 13, 2010
Tips for a great answer:
Dec 08, 2015 | Williams Heating & Cooling
Nov 08, 2013 | Thermos 3509622 Heater
Feb 12, 2013 | Williams Heating & Cooling
Nov 04, 2011 | Williams 2509612 Ceramic Mid-Size Heater
Oct 18, 2010 | Heating & Cooling
Feb 20, 2010 | Williams 1403622 Gas Compact Heater
Jan 22, 2010 | Williams 2509612 Ceramic Mid-Size Heater
Dec 09, 2009 | Williams Heating & Cooling
Dec 12, 2008 | Williams 2509612 Ceramic Mid-Size Heater
80 people viewed this question
Usually answered in minutes!