Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It's one of two issues; either the wiring to the thermostat is incorrect, or possibly you have an open ground. Depending on your system the wires at the thermostat end might have to pair up on one lead. go to where your unit is and look at the schematic for the control board, it will let you know what color you are looking for on the blower lead -- then make sure the corresponding color matches at the thermostat. Knowing the make and model of you unit and the board on it would allow me to be more specific, hope this helps you out some in the meantime.
Posted on Jun 17, 2009
As long as this is a 24 volt thermostat, remove the thermostat from the sub base and connect the wires that are connected to terminals R & W. If the furnace works the problem is in the thermostat. Have you tried new batteries
Posted on Oct 29, 2009
If you just installed the stat, you need to enter installers programing to set it up. To do thi, press and hold "UP" and "FAN" until a number on the left and right show up. The left number is the function and the right number is the setting. You do not specify what type of system you have, so i cannot tell you exactly what settings. But here is a link to the installers manual. the installers program settings is about half way down. http://www.forwardthinking.honeywell.com/related_links/thermostats/focuspro_6000/install/69_1920es.pdf
Posted on May 09, 2010
Tips for a great answer:
Dec 17, 2016 | Honeywell Heating & Cooling
Nov 09, 2010 | Honeywell Programmable Thermostat Heater
Apr 29, 2010 | Honeywell Programmable Thermostat Heater
Feb 06, 2010 | Honeywell Programmable Thermostat Heater
Oct 29, 2009 | Honeywell Electronic Programmable...
Jun 17, 2009 | Honeywell Focus 6300B 5-2 Days...
Jun 12, 2009 | Honeywell Electronic Programmable...
Apr 14, 2009 | Humidifiers
Jan 01, 2009 | Honeywell Electronic Programmable...
Nov 24, 2008 | Honeywell Electronic Programmable...
18 people viewed this question
Usually answered in minutes!