Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It sounds like you have your gages hooked up wrong. Blue goes to the Suction line (the big line) it should be cold when the units running.
Red goes to the liquid line (the little line).
Posted on Apr 27, 2009
I have scroll chiller contains scroll compressor tandom circuit. One of the compressor failure from it due to unbalance of the winding. Previously compressor thermistor opens two to three times. Also one phase open in contactor of the compressor. Can you guide me regarding the reason of compressor failure and what is the next step for the replacement of compressor. Also give guide line for the points take care.
Posted on Mar 27, 2010
Tips for a great answer:
Oct 10, 2016 | Carrier Heating & Cooling
Jul 31, 2016 | Carrier Heating & Cooling
Feb 13, 2014 | Intertherm Heating & Cooling
Jun 17, 2011 | Heating & Cooling
Jun 07, 2011 | Carrier Heating & Cooling
Aug 06, 2009 | Comfort-Aire HMC36AT-1 Air Conditioner
Jun 07, 2009 | Carrier 38CKC036 Air Conditioner
Jan 04, 2009 | Carrier 52CQ-312-4 Comfort Series Heat...
Dec 03, 2008 | Carrier Heating & Cooling
Jan 16, 2018 | Heating & Cooling
32 people viewed this question
Usually answered in minutes!