Question about Electrical Supplies
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
hook up the red to red
black to black
green to bare wire
tie white wire to other whites in back of switch box in the wall.
If no whites in there cap it off with a wire connector.
Posted on Nov 03, 2008
SOURCE: Single Pole Dimmer Installation
I'm not sure if this is going to work in your case, but I'm pretty sure it will...
Green to ground (probably bare)
Black to black
White to the red that's not labeled 3-way
wire nut on the red labeled 3-way
That should fixya!
Posted on May 30, 2009
house has a black and a white line and a ground commper, dimmer has two black and a green
How do I know which blck lead goes to white and which goes to black? One lead is shorter than the other.
Posted on Aug 09, 2009
You are correct in assuming green is the ground and connects to bare copper wire. Black is always the HOT wire and should be attached to the black wire. Red wire connects to white wire.
Posted on Sep 13, 2009
Tips for a great answer:
Jul 25, 2015 | Leviton Electrical Supplies
May 14, 2014 | Leviton 5634 Dual 1 Pole Switch Decora...
Mar 02, 2014 | Leviton Electrical Supplies
Mar 08, 2013 | Leviton Anywhere Switch - 6696-W - White
Sep 24, 2011 | Leviton Trimatron Rotary Dimmer 6602-i Lot...
Sep 10, 2011 | Leviton Electrical Supplies
Mar 07, 2010 | Leviton Rotary Dimmer 6683-i Ivory 3-way...
Sep 29, 2009 | Leviton Trimatron Rotary Dimmer 6602-i Lot...
688 people viewed this question
Usually answered in minutes!