Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a problem with
Buy a new ignitor either from the ignitor store online, or your local distributer, Contracter, dealer.. they usually run from 15 dollars to 35. Their simple to change out and deffinite do it yourselfer... Oh and turn off power at breaker panel, you don't need any unexpected surprises!!
Posted on Dec 02, 2008
Are you saying you put your face in the burner box and blow air on the burner tubes? You are a braver man than I. Gas pressure or air adjustment. Get a technician to check your system or shave all the hair on your face and head before you burn it off.
Posted on Dec 05, 2008
SOURCE: furnace ignition
The probable cause is the pressure switch. It's a round disk either silver or black in color. They can stick in either the closed position or the open position depending on what your unit needs to fire. You can take the rubber hose off from the inducer motor and blow lightly and **** in lightly to make sure the switch is free from debris. Then try again and if it continues, then you will need to replace the switch. It can also be a limit switch that is going bad as well.
Posted on Mar 16, 2009
if your power vent moter is not running you should not have have glowing ignitor.Frist the vent moter must close an air prove switch in series with the idnitor .seems you have a stuck air prove switch.Its the one with a hose attached
Posted on Apr 07, 2009
Tips for a great answer:
Dec 05, 2017 | Heating & Cooling
Nov 01, 2017 | Goodman Heating & Cooling
Nov 18, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Jan 25, 2018 | Heating & Cooling
Feb 28, 2011 | Heating & Cooling
Jan 17, 2011 | Heating & Cooling
Apr 15, 2010 | Heating & Cooling
Dec 30, 2009 | GE Ovens
Dec 29, 2009 | Heating & Cooling
Dec 06, 2009 | Heating & Cooling
79 people viewed this question
Usually answered in minutes!