Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It may be, Rinnai suggests a maximum length of about 13 equivalent feet of venting including elbows. Add 6 feet for every 90 degree elbow. If the vent is longer than this it is taxing the combustion fan motor and it will start giving you error codes and will not ignite. Remove the trim panel from behind the heater and find the flexable air intake pipe. Temporally remove it from a fitting and test the unit a few times to see if the unit starts quieter. This procedure will be taking room air into the heater for combustion and circumventing the direct vent feature of the heater, not a fix. Have you had the gas pressure tested? It gould be that! You may wish to consider relocating the heater and fire your installation contractor for putting you in this predicament, not Rinnai.
Posted on Nov 05, 2009
Testimonial: "Thanks very much. Please see comments."
Tips for a great answer:
May 11, 2015 | Heating & Cooling
Apr 26, 2015 | Rinnai Heating & Cooling
Sep 17, 2011 | Heating & Cooling
Mar 10, 2011 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Nov 05, 2009 | Heating & Cooling
Jul 29, 2009 | Rinnai EnergySaver 556 Air Conditioner
Dec 05, 2008 | Rinnai RHFE-556WTA Direct Vent Heater NG...
Aug 04, 2008 | Heating & Cooling
Jun 15, 2008 | Rinnai Toyostove Direct Vent Heater: Laser...
50 people viewed this question
Usually answered in minutes!