Question about Heating & Cooling
I have a GE central air unit model 5kcp39lg S407 s. when I got home this evening and turned the ac on I noticed that it wasn't getting cold. after looking at the unit outside I noticed it wasn't coming on anymore. what could be the problem and possible solution verses having to purchase a new one?
First check the breakers for the condensing unit (outside unit) and the disconect outside by the unit (could be a breaker ,a pull off/on switch or fuses)If its ok , you should have 220 ,240 volts to the unit contactor (you'll see it after removing the cover on the condensing unit).When the termostat is in the cold position and the temperature its set is lower than the one inside the house the contactor should be pulled in and give power to the compresor and the fan.But if the termostat is in the cooldest set and the blower inside the house works and the contactor in the condensing unit is not pull in the problem is in the termostat or in the low voltage wire.
Posted on Apr 24, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 29, 2015 | Heating & Cooling
Jun 15, 2014 | Goodman Heating & Cooling
Jun 09, 2012 | 2004 Lincoln LS
Apr 28, 2012 | GE Ahm18dp Air Conditioner Window Unit...
Jun 23, 2011 | Goodman CKL42AR42 Air Conditioner
Jun 22, 2011 | Heating & Cooling
May 09, 2011 | Heating & Cooling
May 18, 2009 | Heating & Cooling
Jan 02, 2008 | GE Quiet-Aire Ductless Split System Air...
Aug 21, 2017 | Heating & Cooling
203 people viewed this question
Usually answered in minutes!