Question about Goodman Heating & Cooling
I will give a few basic and easy steps of things to check first.
1. If your air handler has a float switch either attached to the secondary 3/4 pvc drain, or to secondary drain pan, check to make sure the water level hasn't risen and activated the float switch. if it has, you will have to flush the primary drain line and/or primary drain pan(located inside the air handler).
2. Check to see if the air handler is running(blowing air). if not, you'll want to check the breaker for the air handler- it might have tripped. if not tripped, you could have a bad 24v control transformer(inside air handler), or bad thermostat.
3. If the air handler is running, you can go outside to check for a red reset button located on the outside unit, usually near the bottom. Sometimes when the coils are dirty, or the outside fan motor stops working due to a bad motor or capacitor, the pressure of refrigerant will rise and cause the reset button to trip. If its tripped and you reset it, and if the unit starts, check to make sure outside fan is running and coils are clean. If unit does not start, check the outside disconnect/ breaker to make sure it is on and/or not tripped. If you have a volt meter, you can check for 240volts. This is only if you know how to use a volt meter safely without getting electricuted. If power is present, then it could be the compressor contactor, or the dual capacitor, located in the outside unit, which operates the fan and compressor, and could be checked with a capacitance meter and/or a vom with a capacitor tester. Some signs of a failed capacitor is when the top part seems kind of rounded and bubbled up, or when there is gel leaking from it. Remember, do not touch the terminals of a capacitor, even if the power is off, capacitors can hold electricity for a long time. (days, months, even years)!!!
Posted on Nov 11, 2013
Might be it is relay problem in pcb. Pls check the cord then relay by a technician,
Posted on Oct 15, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 29, 2010 | Goodman GPC1342H21A Air Conditioner
Jan 06, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jul 06, 2009 | Dometic Rooftop RV Air Conditioner
Jun 12, 2009 | Heating & Cooling
May 28, 2009 | Heating & Cooling
May 02, 2009 | Heating & Cooling
Jan 09, 2009 | Friedrich QuietMaster Electronic SS12J30D...
Jun 15, 2008 | Samsung AS18A6RB Air Conditioner
Oct 27, 2007 | Ruud UBHC Air Conditioner
119 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: