Question about Electrical Supplies
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
well lets see on one side you should have two brass screws that would be to interupt your lead to the fixture then you either have a brass and silver screws on the other side or you have black and white wires the black or brass is always hot the silver or white is neutral does that answer your question if not hit me back with a description of what your switch looks like
Posted on Jun 27, 2009
WARNING: Do not attempt to do this work unless you completely understand the information provided below. If in doubt call an electrician.
Always make sure the power is disconnected from all possible sources before making any connections. Your description of the problem indicates that there may be multiple power wires coming into the same box. In that case local codes may require that the box be partitioned to prevent exposure to voltages up to 220 volts.
You need to determine where each wire goes to know how to connect them together. You cannot rely on color alone. If the power supply runs through the box to the loads then most (but probably not all) of the white wires will be connected together. If the power runs to the load boxes first then none of the white wires in the switch box should be connected together. They are used to run the switched/dimmed power back to the loads (and should be taped to cover the white in the box). In that case each switch has its own power input and they should not be tied together. A wire (could be black or white with black tape) brings power from the load box, gets connected to the input terminal of the switch and the corresponding black wire carries the switched power back to the load. The fan/light switch will have one power in and a switched power out for the fan and another for the light. The 3-way will have one "power" in (or it could be the final power out to the light) and two "carrier wires that connect to the other 3-way switch. If the power supply goes through the switch box then there will be at least 10 wires in that box. In that case see the attached diagram:
Posted on Sep 23, 2009
I opened the box and traced the lines to see which are connected
when the switch is turned on and I left the red wire disconnected.
Posted on Jan 29, 2010
you need 2- 3way switches to work properly, on the one side of the switch there are 2 screw terminals and your "traveler wire pair" are connected here,then on the same switch with only 1 terminal on that side the hot phase hooks to one switch and the other switch has the light and neutral hook to this switch
Posted on Feb 14, 2010
Tips for a great answer:
Dec 01, 2013 | Cooper Wiring Devices Electrical Supplies
Apr 04, 2013 | Cooper Wiring Devices 6009W-K ROTARY...
Nov 04, 2012 | Cooper Industries Cooper Wiring 274V...
May 25, 2011 | Speed Ceiling Fan 3-speed Switch By...
Nov 09, 2010 | Cooper Wiring Devices Aspire Smart Dimmer...
Jan 27, 2010 | Cooper Industries Cooper Wiring 9534DS...
Aug 07, 2009 | Electrical Supplies
Feb 08, 2009 | Cooper Wiring Devices Three Way Grounded...
58 people viewed this question
Usually answered in minutes!