Question about Heating & Cooling
I have a coleman 2 in one self igniting furnace. It runs the ac and the heat. It will push the ac just fine through the vents but it wont push the heat. THe flame is just as big, the furnace itself pushes out heat, but its not getting through the vents at all in the trailor.
I take you mean there is a fan coming on that blows AC air thru the vents and is the same fan used to blow the heat ? If that is the case is the fan coming on when the heat comes on ? If not then that is why you are not getting the heat.
That can be from a temp sensor not working or a control board or a contactor
First see if the fan even comes on or if the same fan is used for both AC and heat
Posted on Oct 20, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Flame Adjustment
Make sure the unit is operating on the correct gas, Natural or Propane (LP). The sound you are experiencing is either not enough gas and the flame is burning inside the burner port(s) or too much gas and the flame is much larger than it has to be. At any rate, get a technician to check the gas pressure entering into the home. NOW!
Posted on Sep 18, 2007
SOURCE: coleman furnace wont fire
Check inside the door panel next to the wiring schematic, you should find the diagnostic codes. Look up 7 blinks. This should narrow down the problem. ( It sounds like a bad hot surface ignitor).
Posted on Apr 10, 2009
The flame sensor is not working properly, it is not allowing the ignitor to ignite, and this is making the system shut down, the flame sensor has obtain a build up of carbon, you will need to remove the flame sensor, and take a little piece of sand paper to remove the black carbon from the flame sensor stem, clean until the stem is shinning, replace the flame sensor and turn the furnance back on this will correct the problem.
Posted on Dec 14, 2009
My furnace did not have a reset switch on that particular limiter. I unpugged the switch, it had 2 wires, waited 15 seconds or so and then plugged it back in . Turned the furnace back on and the limiter reset itself.
Posted on Dec 24, 2009
Tips for a great answer:
Mar 02, 2017 | Coleman Heating & Cooling
Jan 29, 2014 | Goodman GMS90703BXA Heater
Jun 05, 2017 | Heating & Cooling
Jan 01, 2013 | Coleman Home Electric Furnace Eb15b/Eb15d
Feb 10, 2011 | Coleman Propane Forced Air Heater...
Jun 13, 2017 | Coleman Heating & Cooling
Dec 09, 2009 | Coleman Propane Forced Air Heater...
Mar 31, 2009 | Coleman Propane Forced Air Heater...
Jan 13, 2009 | Coleman Propane Forced Air Heater...
May 30, 2008 | Heating & Cooling
160 people viewed this question
Usually answered in minutes!